Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
try checking the pressure sensing switch,it has a tube that should run somewhere close to the inducer fan.sometimes this hose fills with liquids,and makes the units act funny.I don't know if you have a condensing unit or what.the furnace wont try to light if it cant tell the inducer motor is running.any induced draft unit will work this way.you can also do a temp. bypass of the pressure switch to make sure the contacts on it are closing just be sure your inducer fan is running,and you cant leave it like that its just a test.that is a safety feature you really need.
Posted on Mar 19, 2009
NO BECAUSE THE BOARD IS TELLING THE FANS TO STARTARE THE CONTACTS FUSED TOGETHER OR STUCK IN THE CLOSED POSISTION CHECK THIS FIRST
Posted on Aug 10, 2009
need help with gas furnace put in new presure switch and it worked for a while now i have to blow into it to get it to turn on ignitor .
Posted on Dec 10, 2009
When a furnace is replaced with a newer style unit like yours with an inducer motor, they sometimes use the old vent pipe. These old style vent pipes are transite (light weight cement), the moisture created from your furnace exhaust is caught on the cool transite surface and runs back down into the blower blades or wheel bringing a white mineral deposit with it which causes your problem. The vent should nave been replaced with the heater using a metal vent material. You will need to replace your inducer motor assembly and vent pipe to prevent a recurrence.
Posted on Dec 30, 2009
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Feb 15, 2015 | Heating & Cooling
Jan 17, 2015 | Gibson Gas Furnace 60000 Btu 90% Afue...
Jan 24, 2014 | Fedders Heating & Cooling
Jan 02, 2014 | Heating & Cooling
Mar 03, 2013 | Omega Trane Furnace Draft Inducer Blower...
Oct 22, 2010 | Heating & Cooling
May 04, 2010 | Goodman GMS90703BXA Heater
Dec 04, 2009 | Omega Trane Furnace Draft Inducer Blower...
Jan 26, 2009 | Goodman GMS90703BXA Heater
31 people viewed this question
Usually answered in minutes!