Question about Empire Heating & Cooling
Pilot light wont stay lighted, when blower fan kicks in, the pilot light goes out
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Unable To Keep Pilot Light Lit!
I have a Williams top vent gravity wall furnace (model 5009622) and I had the same problem. I had to take the cover off the furnace -- screw on top and two at the bottom (open the access door and there is one screw on each side) to get to the reset button for the vent safety shutoff system. On my furnace it's on the left side toward the top of the unit. I pressed the little red reset button and it's been working ever since. If your furnace is properly installed and doesn't have bird's nest in the chimney, it should work fine. Good luck!
Posted on Dec 06, 2007
I am not familiar with this heater but it sounds like it could be a blockage in the main gas line into the heater or perhaps a blockage to the pilot gas line and maybe starving for gas. Best bet first is to check the main gas line from the heater. Easiest way to do this is to remove it from the heater and blow it through with compressed air. Then try the heater again. If that doesn't fix the problem then you can try blowing compressed air down through the pilot line. Could be a little dirt creating a blockage there. Then try the heater again. If it still does the same thing then try removing the panels to expose the heater's piping. If you can remove the main pipe into the heater from the gas and blow compressed air through it it should clear any obstruction from both the main line and the pilot. If this doesn't work then I would think you have a more severe problem and will need to take it to your local Heater Repairer. Hope this helps.
Posted on Dec 22, 2007
The power pile (pilot generator) is defective. It produces a milivolt signal to ensure to keep the gas valve open. If it goes bad, the valve thinks the pilot is out, even when you are holding the button down, so when you release the button, it shuts the gas off to prevent excess gas buildup and a possible explosion.
Posted on Sep 12, 2009
weak pilot flame: should wrap around therocouple.
blue flame with yellow tip not yellow and lazy.
if flame good replace thermocouple
Posted on Oct 26, 2009
It sounds like the gas valve is dropping out. Make sure the system is venting the exhaust(no restrictions). Then make sure all your wiring connections in the unit are tight. In a millivolt system if all wiring connections aren't tight and clean your circuit will drop in millivolts and the gas valve will drop out. The gas valve requires a certain millivolt to stay open. I hope I was of some assistance!! Good luck!!
Posted on Nov 29, 2009
Tips for a great answer:
Nov 14, 2014 | Empire Comfort Systems Empire Tahoe Deluxe...
Mar 04, 2014 | Empire Comfort Systems RH-65BLP 65,000 BTU...
Jan 29, 2011 | Empire DVC-35 Wall Mounted Panel Heater
Nov 24, 2010 | Heating & Cooling
Oct 07, 2009 | Reddy Heater-10-12-15,000 Btu L.P.
Dec 05, 2006 | Empire GWT-25 Wall Mounted Panel Heater
60 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: