Question about Dayton Permanent Split Capacitor Motor Fan
I need to replace my old Dayton capacitor start 1HP with new Dayton capacitor start 6K321BA 1HP but has different wiring colors ..etc. Need to connect wires, black( hot ), white( neutral ) and green( ground ) to the motor but which?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Installing a Dayton G73
If that is a 240V unit then you are correct wiring L1 and L2 to black and red. Unless the unit uses 120V for something like a control panel, it doesn't need the neutral.
Posted on Jan 14, 2008
Look at the name plate on the motor. If it's 'duel voltage' it will show a 'high' and 'low' voltage hook up. If it only shows one hook up config, then use the rated voltage on the name plate. If 240 volts, use L1 and L2 for incoming power @ 240volts.
Posted on Jun 30, 2009
SOURCE: I have a Dayton 36
GRAINGER.COM THEY HAVE A TECH LINE, BUT ON THE MOTOR LABEL IT SHOULD HAVE THE WIRING DIAGRAM .. GOOD LUCK AND I'FN I WAS ANY HELP PRAISE IS APPRECIATED .. SO VOTE JAY MOTORWIZJ
Posted on May 28, 2010
Tips for a great answer:
Apr 13, 2017 | Dayton Pool & Spa
Apr 11, 2013 | Heating & Cooling
Mar 24, 2013 | Dayton 1hp 1725RPM 56C Frame 90 Volt Dc...
Sep 27, 2012 | Dryers
May 17, 2010 | Heating & Cooling
Nov 21, 2009 | Maytag Neptune MDE5500AY Electric Dryer
Aug 28, 2009 | Dayton Permanent Split Capacitor Motor Fan
Jul 18, 2009 | Plumbing
Jun 17, 2009 | AO Smith A O Smith Motors Century 1hp 115v...
Apr 07, 2008 | Carrier 38CKC036 Air Conditioner
865 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: