Question about Generac Guardian Electrical Supplies
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If this is one of the big "taco cart" portables you need to check that the vent on the gas cap is open when you're running the engine. In the center of the gage on the gas cap is a little knurled knob, turn it counter clockwise (lefty loosey), about a half turn or so and run the generator.
If that doesn't solve your problem add to it here, otherwise please give me a rating I'm trying to build a little credibility here and could use the help.
Posted on Dec 02, 2008
I work on these every day. Its either gonna be the rotor or stater, the voltage regulator, but most likely its a bad stepper motor which is the throttle motor, or control board. Thats all that could be causing that so its one of those. If its the rotor or stater thats bad it causes the generator to RPM up because it thinks its not producing enough power due to that. I had the same problem with the same one we just fixed and it was the slip rings on the end of the rotor so bad rotor.
Posted on Jul 09, 2009
I have a generator that did the same thing. It would start and then stop within a few seconds. The more expensive generators have an oil level safety switch to prevent the engine from burning up. There is usually a wire connecting to the switch on the outside of the engine near the oil fill hole. Remove this wire and try to start the generator. If it runs without a problem then it is the switch. You need to remove the switch and take it apart carefully and clean it. There is a small float inside the assembly. When the oil runs low the float allows the switch to short to ground which kills the spark to the spark plug. Hope that helps.
Posted on Oct 01, 2009
Testimonial: "This is good information in the event that the low oil switch is part of the problem."
Tips for a great answer:
Jun 28, 2016 | Generac Electrical Supplies
Dec 12, 2015 | Generac GUARDIAN Standby Generator 10 kW/9...
Dec 05, 2015 | Generac Electrical Supplies
Oct 15, 2014 | Generac Guardian 8kw Standby Generator
Oct 12, 2013 | Generac Guardian Electrical Supplies
Jan 20, 2012 | Generac 13,000 Watt / 13,000 Watt Home...
Aug 26, 2011 | Generac Guardian 0E4494 - manual/auto off...
Aug 13, 2011 | Generac Guardian RTSE200A3 200 Amp...
Sep 08, 2009 | Generac 100 Amp 120/240-Volt Transfer...
Jun 28, 2009 | Generac Guardian Quietsource 25,000 Watt...
60 people viewed this question
Usually answered in minutes!