Question about Amana Distinctions 95% Gas Furnace Gmh950704cx 69k Btu
Should furnace be turned off?
Posted by Anonymous on
Amana distinctions furnace is the top quality furnace and I would you recommend to get professional technician help for that. You may call in Toronto at 905 201-1293, Clean Air Heat is there to help you out.
Posted on Jan 24, 2013
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: amana furnace
This is no doubt due to failure of the "hot surface ignitor". This device lights the main burners for your furnace, and they fail a lot. I strongly recommend the replacement should be done by a technician.
Posted on Oct 25, 2008
be aware that not repairing this asap that you are causing yourself more problems First I would change out the fan capacitor and see if this could be the problem. Secondly if the capacitor isn,t the problem change out the motor . By continuing to allow the system to cycle like this the compressor will take a dive on you costing more . Good Luck
Posted on Aug 04, 2009
Testimonial: "Yes, it's dual run capacitor problem. I used a stick to spin the fan blades and it starts to slowly spin and up to normal speed, so motor is good."
check to see if the flame rod tip is in the flame(like the hot junction on a thermocouple). the pressure switches are a normally closed switch and a blocked flue could cause them to open. the circuit board should run through the safety switches and check them before the gas is opened at the valve. also the drain lines that you see at the inducer fan should be free of condensation but if the inducer fan has condensation in it, it will open the airflow safety switch. you will hear the crackling noise from the fan. also there should be a trap below the fan that should be full of water to keep the fan from pulling air from the wrong place. I would not suspect the board at this point
Posted on Dec 15, 2009
i have a 10 years old Amana 5 ton AC. The service man syas Ineed an new Coil (leaking freon. He quoted $2700 for the cheapeast one. Can I get a better price by shopping around?
Posted on Apr 18, 2010
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Oct 17, 2015 | Amana Heating & Cooling
Dec 06, 2017 | Heating & Cooling
Mar 12, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 06, 2010 | York Furnace Draft Inducer Blower Fasco #...
Dec 07, 2009 | Goodman Furnace Draft Inducer Blower ...
Dec 04, 2009 | Omega Trane Furnace Draft Inducer Blower...
Nov 28, 2009 | Heating & Cooling
Jan 26, 2009 | Goodman GMS90703BXA Heater
109 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: