Question about Heating & Cooling
I need to replace a blower motor in a Lennox gas-fired home hot-air heater. It is ''chirping'' and I want to replace it before it quits. I have located the correct replacement part, and it looks like a fairly easy fix (insert shaft of motor and hook up two wires). Is this something I should attempt myself after shutting off power to the unit?
It is a fairly simple operation. The hardest part may be seperating the blower wheel from the motor shaft. I recommend first sanding then applying a little oil to the old shaft. Prop the blower housing aprox. a foot off the floor with the motor facing down then using a wrench (NOT pliers as you may scar the shaft) hold the wheel with one hand and work the wrench on the shaft work it back and forth to loosen. DO NOT hammer on the end of the shaft as you will mushroom it ever so slightly. The weight of the motor should cause the shaft to slide down. Good luck and don't forget to answer back if this works or not.
Posted on Jan 18, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2011 | Master Heaters Heating & Cooling
Dec 23, 2010 | Heating & Cooling
Mar 08, 2010 | Heating & Cooling
Jan 03, 2010 | Superior Lennox Blower Thermal Sensor -...
Jan 02, 2010 | 2000 Dodge Caravan
Jul 11, 2009 | Heating & Cooling
Jan 08, 2009 | Superior Lennox Blower Thermal Sensor -...
291 people viewed this question
Usually answered in minutes!