Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Access the installer setup menu (You will need the installation manual from the t'stat to do this) and turn off the "intelligent recovery" feature. This feature turns the equipment on in order to bring the conditioned area up to temp at the set time. Or you could set the "wake time" to 6:50!!!
Posted on Dec 16, 2008
I connected the blue wire to the R and the white wire to the W on the old thermostat and shoved the new Honeywell 5-1-1 Day programmable thermostat up the first guys *** that i ran into at Canadian Tire
Thanks for your help
Posted on Dec 29, 2008
On your thermostat - R is the power in terminal. Y is the cooling out. W is the heating out. (G is fan out). It does not matter which wire goes to R, the other should go to W - if no heat with a call, the thermostat is bad.
Posted on Apr 17, 2009
Tips for a great answer:
Nov 28, 2015 | Honeywell Programmable Thermostat Heater
Aug 04, 2015 | Honeywell Water Heaters
Jan 22, 2011 | Honeywell Programmable Thermostat Heater
Dec 08, 2010 | Honeywell Programmable Thermostat Heater
Sep 02, 2010 | Honeywell Programmable Thermostat Heater
Oct 18, 2009 | Honeywell Programmable Thermostat Heater
Apr 12, 2009 | Honeywell Programmable Thermostat Heater
Sep 19, 2007 | Honeywell HZ365 Ceramic Compact Heater
44 people viewed this question
Usually answered in minutes!