Question about Fasco Heating & Cooling
Its a fan motor i need to hook up the wires
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You almost have it Look closer at the run capacitor. It has Herm, this is for the compressor, Com or C and F or Fan.
1 of your power wires is the fan speed so connect them accordingly usually black is hi, blue med, & red is low. You are "feeding" voltage to the selector switch on 1 side and coming out to the fan motor speeds.
Next you have a "Common" wire on your fan motor (this means its Common to all the other connections inside the fan motor to me. It is usually white. Connect this to the other line of power usually the Com on the capacitor unless it connects to a strip on the selector switch. But 1 of these 2 places will be the other side of your Power when plugged in. Lastly the brown it is usually the fan capicator only wire and it will connect to the fan "F" terminal on the capicator this terminal will not have any other wires connected to it.
This should make you a happy camper. Please rate me accordingly and good luck.
Posted on Mar 08, 2009
The extra wire is a additional speed wire and the existing model that you are installing is possibly not set up for that additional speed. It depends on the exact model of air conditioner that your post says you have, but we can never be sure until you confirm the model number of your Goodman, if its a split unit, a package unit or condenser fan or evaporator fan. Let me know all of those answers and I will help you determine the answer, Thanks, Sea Breeze
Posted on May 08, 2009
SOURCE: I have a Trane XE1200
OK, locate the terminals on the capacitor marked "HERM"(Compressor lead), "FAN", and "COM".(common)
HERM and COM remian as they are.
The wire going to "FAN" (usually brown) will be placed on either terminal of the new capacitor. (This is the ((usually brown)) wire comming off of the fan motor.) An additional wire needs to be run from the other terminal of the new capacitor to the "COM" on the old capacior.
What you are doing is bypassing the fan side of the old capacitor but still using the compressor side of the old Cap.
The fan should have a wiring diagram on it to help identify the wires if there is no brown wire. The other two wires will be identified on the wiring diagram as well, but one typically goes to the contactor and the other to the board.
Posted on Sep 07, 2009
There should be a small set of screw lugs on the electronic board in the furnace. Look for a red wire that comes out of the transformer and follow it to find where the 24V connections are.
Posted on Sep 26, 2009
Tips for a great answer:
Jul 01, 2014 | Ruud Rheem 1068-311 Furnace Control Board...
Aug 15, 2013 | Ruud UBHC Air Conditioner
Aug 24, 2011 | Heating & Cooling
Sep 20, 2010 | Heating & Cooling
Aug 13, 2010 | Heating & Cooling
Jul 20, 2010 | Aloha Housewares (93645) Ceiling Fan
Sep 21, 2009 | Ruud UBHC Air Conditioner
Jun 04, 2009 | Ruud UAMB Air Conditioner
May 30, 2009 | Heating & Cooling
May 19, 2009 | Heating & Cooling
32 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: