Question about McCulloch Electrical Supplies
Cost of generator to buy
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need to trace out the power wires the come out of the genset. They will end up on a breaker. With a volt meter measure both sides of the breaker. If one side has voltage and the other side doesn't, then your breaker is opened. Press the breaker in closed to see if it actually closes. If it don't then you will need a breaker. However, if no voltage is being produced, it is possible that the voltage regulator let go.
Posted on May 09, 2009
I did not understand how you turn on generator, as it is always turned on.
If you use the ON/OFF switch it is stopping the prime mover.
If you reset the AC breaker without load, and it stops - it means that you have short circuit after the breaker. Check the output receptacles.
Try this link:
Posted on Jun 14, 2010
If you could not start in spite of oil and gas change, checked gas supply, spark plug, ignition cables and coils (magnetos) and so on whitout success, then try this:
Your generator has a low oil level protection, which stops the ignition of the motor.
After "a couple of years" sitting without or with old oil, the level switch may have got lazy or stuck down.
If your oil level seems to be good, while measured, find the oil switch and try to shorten or disconnect it.
If you succeed in running the generator change or repair the oil switch.
I hope that this will be helpful, because I don't have your device in front of me, but some people rank such an answer with 2 thumbs, which means useless. Better dont rank.
Posted on Jul 24, 2010
The spark coil is bad if you have no spark
Small engine repair. Part is expensive.
Have you checked spark for sure?
1) Spray WD-40 directly into carburetor
If machine has spark, it will fire
2) Is exhaust port clogged with carbon and dirt?
3) Get new spark plug
Pull out old spark plug
Put spark wire on plug
Hold spark plug wire with fingers
Put spark plug threads against metal opening where spark plug came out.
Metal to metal
Pull cord or push starter
Look for spark between metal
No spark, then spark coil is bad.
Posted on Oct 26, 2010
SOURCE: I need a spark plug
Hi and welcome to FixYa. I am Kelly.
The standard plug is an NGK "BPR5ES" or Denso "W16EPR-U" There are a number of alternate plugs out there if you use the number above in a cross reference book.
One thing to note... the generator has a "Low Oil" sensor and if the oil level is low you will not see any spark. If after you install a new plug and you still do not have spark... un-hook one wire from the low oil level sensor and check spark again. If you unhook the sensor wire knowing full well the oil level is full.and have spark; the sensor is either dirty or bad.
Thanks for choosing FixYa,
Posted on Feb 19, 2011
Tips for a great answer:
Jan 21, 2016 | McCulloch 11 HP 5700 WATT GENERATOR
Nov 24, 2014 | Electrical Supplies
Aug 07, 2014 | McCulloch FG6000MK - Generators - Portable...
Aug 28, 2012 | McCulloch 11 HP 5700 WATT GENERATOR
Oct 17, 2011 | McCulloch FG6000MK 5700Watt 13 HP 338CC...
Aug 23, 2011 | McCulloch 13HP 338 Cc Portable Generator #...
Mar 04, 2011 | McCulloch FG6000MK 5700Watt 13 HP 338CC...
Jan 03, 2011 | McCulloch FG6000MK 5700Watt 13 HP 338CC...
Oct 25, 2010 | McCulloch 13HP 338 Cc Portable Generator #...
64 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: