Question about Heating & Cooling
Sounds like your fan switch is defectiveor posibble installed in the wrong place. This switch is heat controlled and delays the fan coming on until there is warm air to blow.
Posted on Dec 31, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Mostly likely the problem is in the pressure switch that tells the board that the blower started and it is okay to fire the burner. The pressure switch is usually a 2" or so round thing about 1" thick, it will have one or two tubes coming out of it that go to the blower or heat exchanger. Make sure that the tube is not cracked or that it has not come off at either end.
The pressure switch can be jumped out to check out if that is the problem, but you need to jump it out after the cycle has started and the switch needs to open after a cycle for the heater to refire again, so that fix would be very temporary. But it may tell you for sure what the problem is.
Posted on Nov 14, 2009
Tips for a great answer:
Nov 19, 2012 | Goodman Heating & Cooling
Oct 06, 2012 | Heating & Cooling
Jun 20, 2017 | Heating & Cooling
Oct 20, 2011 | York Furnace Draft Inducer Blower Fasco #...
Mar 11, 2010 | Heating & Cooling
Nov 14, 2009 | Heating & Cooling
Jun 20, 2009 | York Furnace Draft Inducer Blower Fasco #...
Dec 26, 2008 | York Yankees Bedding MLB Comforter
Oct 17, 2017 | Dimplex Heating & Cooling
89 people viewed this question
Usually answered in minutes!