Question about Heating & Cooling
No problem have done this many times. R from the t-stat goes to R on the indoor unit. G goes to G Y goes to Y and C goes to C if you have a C or the t-stat the you are using. If there is no C there dont worry about it. It only need to be hookup if the t-stat uses power from the unit to run. Many t-stats today use battery power and do not need the C wire hooked up. Now R and C from the outdoor unit. R goes to the Y on the indoor unit and C goes to C on the indoor unit. That means that you may have two wires under the Y terminal and sometimes under the C terminal on the indoor unit. If on the outdoor unit there is no designation of R and C dont worry, just hook one wire to each of the two wires there for your low voltage connection. It does not matter which one goes to which unless they are marked then it may matter.
This should get you up and running and see it really isn't that hard!! :-)
Posted on Nov 14, 2009
Testimonial: "Thank you very much! I have been searching the inernet for hours to find a manual or diagram. Got a response within 15 minutes of posting. "
Bad or dirty flame rod.
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Jan 10, 2010
Tips for a great answer:
Sep 23, 2013 | Rheem Ruud Weather King Corsaire Rheem...
Oct 23, 2011 | Ruud UBHC Air Conditioner
Jul 10, 2011 | Ruud Heating & Cooling
Feb 15, 2011 | Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 10, 2011 | Heating & Cooling
Jan 03, 2011 | Ruud Heating & Cooling
Jun 04, 2009 | Omega Trane Furnace Draft Inducer Blower...
Jan 13, 2009 | Heating & Cooling
Jan 19, 2008 | Ruud UBHC Air Conditioner
May 24, 2017 | Heating & Cooling
575 people viewed this question
Usually answered in minutes!