Question about Goodman GMS90703BXA Heater
The ignitor/glow light comes on, the flames/burners light, the glow light goes off and then the burners run for maybe 10-15 seconds and the flames go out. Then the process starts over. What is the most likely trouble spot?
The flame sensor is dirty. You can not see the build up on the sensor but enough build up will change the resistance and the furnace thinks there is no flame.
To clean the sensor, first you need to locate it. it will be a sensor located in the path of one of the flames. Once you locate the sensor, open the bottom panel to turn"off" the furnce. After the panel is removed, unscrew the sensor from the frame above the jets. Use a clean rag and gently wipe the sensor several times. Place back in the cut out and close the lower panel.
The furnace should cycle on and the flame stay on for the normal cycle.
Posted on Jan 18, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 05, 2013 | Goodman Heating & Cooling
Jan 23, 2011 | Goodman GMS90703BXA Heater
Nov 13, 2010 | Goodman Heating & Cooling
Mar 05, 2010 | Goodman GMS90703BXA Heater
Feb 26, 2010 | Goodman Heating & Cooling
Dec 08, 2009 | Goodman GDS80904BNA Open Flame Heater
Oct 18, 2009 | Goodman Heating & Cooling
Mar 28, 2009 | Goodman GMS90703BXA Heater
Jan 27, 2009 | Goodman GMS90703BXA Heater
Dec 05, 2008 | Goodman GMS90703BXA Heater
379 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: