Question about Goodman GMS90703BXA Heater
Unit shuts off on reaching heat setting but ID Motor continues to run. Unit heater and blower sometimes restarts when thermostat signals a need for heat, but other times not and status light gives two flashes to indicate the pressure switch is stuck closed (ID Motor still running). The pressure switch was replaced but still get same situation.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The board is bad. The unit thinks a flame is present, so it tells the blower to come on. Replace the board.
Posted on Oct 08, 2009
it sounds like the low temp limit switch, the one that cools the furnace down with the burner off and the thermostat open, when it cools to a point the fan stops, the other switch in burner area turns burner off/on, hope this helps
Posted on Jan 31, 2010
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Dec 05, 2013 | Goodman Heating & Cooling
Oct 15, 2013 | Heating & Cooling
Jan 07, 2011 | Goodman GMS90703BXA Heater
Jan 31, 2010 | Goodman GMS90703BXA Heater
Oct 07, 2009 | Goodman Heating & Cooling
Jan 26, 2009 | Goodman GMS90703BXA Heater
Jan 13, 2009 | Omega Trane Furnace Draft Inducer Blower...
Oct 25, 2008 | Heating & Cooling
113 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: