Question about Carrier Heating & Cooling
My air conditioner recently had its control board replaced, and is now out of warranty. Since the replacement, the unit turns itself off spontaneously, or sometimes flips mode from cool to heat. Any easy fixes?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Air Conditioner malfunction
Hi, Sounds like you have a short in the control circuit to me. Turn off all power going to the unit. Write down or otherwise mark the wires leaving the control board going to the thermostat. Remove them from the control board. Replace the fuse. Turn power back on and see if the fan still runs. If it does, check and or replace the heat limit switch that brings the fan on during the heat cycle. It may just need adjusted. If the fuse blows, I would think that the control board is probably bad. If it doesn't blow, Remove the thermostat. Leaving all thermostat wires open check them with an Ohm meter. There should be no continuity between them. Twist all the wires together at one end and ohm them again at the other end. You should have complete continuity on all wires. If the wiring checks out, down power the unit. Double check your wire colors and rewire the control board. With all wires open at the thermostat, turn the power back on. Touch the RED wire to the YELLOW wire. The Condensing unit should come on. Touch the RED wire to the GREEN wire. The fan should come on. Touch the RED wire to the WHITE wire. The heat should come on. Down power the unit. Replace the thermostat. Test unit. If the fuse has lasted ok but blows now it is either wired wrong at the Thermostat or the thermostat is bad. I hope I have helped. NOTE: If you can not understand these instructions. Call a licensed Heating / Air conditioning company. kstfas
Posted on Sep 23, 2007
Go to the manufacturer website and try and find their download page for the manuals or literature. If they don't have a download, you will have to contact them either by phone or email. They should be able to mail or fax you one.
Posted on Apr 07, 2009
I have that model Air conditioner with remote. Although the remote is marked Admiral thats the only identifying marks on the outside. Here are pictures of the remote.
Battery Compartment Cover
Here is what is printed on the battery compartment cover label.
SHUNDE HUA AO
ELECTRONICS CO., LTD
Drawing No: DF11F1-01 (AL) KYK-1801
Part No: 814011422
Hope this helps. You might try a company called Vance Baldwin they usually carry a large inventory of remote replacements for all kinds of applicances. Had to get a remote for my Panasonic DVD player and it was only $12.00 (brand new)
Posted on Jun 02, 2009
If you are talking about the indoor fan it is probably a bad capacitor. Replace the fan motor capacitor. And YES, if the fan motor needs replacing too, you can DO-IT-YOURSELF.
Posted on Jul 05, 2009
SOURCE: heating problem
Hi Radan, Did you get this problem solved? We have an Electrolux Kelvinator Split System and ours is doing exactly the same thing. I am struggling to find a solulution. Would be great if you can offer any advice.
Posted on Sep 25, 2009
Tips for a great answer:
Nov 25, 2013 | LG LAN186HV / LAU186HV 18,000 BTU 15 SEER...
Jan 05, 2012 | Carrier XHB123D X/Y Series Heat/Cool Air...
May 24, 2010 | LG Heat cool Window Air Conditioner
Dec 06, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 21, 2009 | Heating & Cooling
Jul 06, 2009 | Dometic Rooftop RV Air Conditioner
Feb 05, 2009 | Mitsubishi MSH09TW Air Conditioner
Jan 16, 2009 | Heating & Cooling
Dec 14, 2008 | GE Zoneline AZ55H07D Air Conditioner
Mar 05, 2008 | Mitsubishi Mr. Slim MXZ30TN Air...
56 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: