Question about Heating & Cooling
The compressor won't turn on
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check each screw on your compressor to ground (compressor case). Should be very high resistance Then check the resistance across your teminals on the compressor to be sure it is not shorted. Then check the wiring to your capacitor (The big one). I ran across this just last week. The mechanic didnt have the capicator wired correctly. If it is brand new it will have a wiring schematic somewhere on it.
Dont leave the compressor on very long, but turn it on long enough to get a voltage reading across the terminals. I assume it should be 240 volts. If you have check all of this, they make a jump start gadget to start a stuck compressor. They sell it just about everywhere. Let me know how this comes out..
Posted on Sep 30, 2008
signal of indoor
1、Check whether two sets of plugs on the outlet end of
the motor have loosed from the socket of the
electric control board, insert it firmly when loosing.
2、Check whether the indoor motor has damaged, the
motor should be replaced when it is damaged
3、 Check whether the controllable silicon and other
components on the electric control board have
damaged, replace the controllable silicon or electric
control board when they are damaged.
Posted on Jun 26, 2010
SOURCE: I'm looking for an enigma
E5 Communication errorbetween outdoor and indoor. Check output (call) from your indoor unit to out door unit by Volts meter. If no power in out door, you have to check setting of temp whether it's 23 and less than that and also mode in "Cool".
If power is there in out door and fan only running means compressor is tripped by overheated
Posted on Dec 16, 2010
Tips for a great answer:
Jun 03, 2014 | Pioneer Ductless Mini Split INVERTER Air...
Sep 03, 2012 | LG LMN096HVT WaMounted Mini Split Indoor...
Jan 16, 2011 | Heating & Cooling
Jun 12, 2010 | Heating & Cooling
May 27, 2010 | LG LSC183VMA Split System Air Conditioner
Sep 30, 2008 | Sanyo 24KS62R Cool Mini Split Air...
192 people viewed this question
Usually answered in minutes!