Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I got the same problem in Samsung aircon. The unit I purchsed died slowly. After that Samsung replaced it with the one have the same problem. They are swearing that the green light blinking problem as a normal function and refusing to fix. Their user manual says it is a problem. I think the affected consumers should join hands to take legal action against this scam.
Posted on Dec 20, 2011
SOURCE: the led panel on the
C6 - compressor run current high
- check [resistance of] compressor windings all equal 1 to 4 ohms
- check [resistance] to earth 50 Mohm minimum
- check run current
I'd also check the motor capacitor(s) , In maximum, it is due to weak capacitor. Replace and try.
Posted on Dec 16, 2010
F-6=High discharge temp/overheating compressor.
Due to condenser block (Clean it),/less RPM of fan motor (Replace capacitor)/Noncondensable gas( Remove gas flush out system, vacuum and do gas charging..
Posted on Jan 02, 2011
SOURCE: Hi my LG healthplus inverter
Indoor Pipe Sensor or Outdoor Sensor Assy fault, Open or Short. Disconnect from PCB and measure resistance. Air sensor = 10 kOhm at 25C, Pipe sensor = 5
kOhm at 25C. If not replace sensor
Posted on Jan 20, 2011
We have an Amcoraire 12,000btu mini split. The heat doesn't seem to be working. We can hear it trying to go on, the outside unit fan runs, but nothing comes out of the inside unit at all. This doesn't seem to be affecting the a/c part and we get no error codes. Is there something wrong with our unit?
Posted on Feb 19, 2011
Tips for a great answer:
Jul 12, 2017 | Inverter Heating & Cooling
Jul 29, 2016 | Inverter Heating & Cooling
Sep 30, 2015 | Inverter Heating & Cooling
Jul 12, 2014 | Heating & Cooling
Apr 23, 2013 | Heating & Cooling
Dec 16, 2010 | Heating & Cooling
Jan 17, 2010 | AmcorAire UCHW-H12AF2 Split System Air...
726 people viewed this question
Usually answered in minutes!