What should my humidifier be set at for the winter?
I'm no expert, but those who are seem to agree that the first thing to check is your evaporator panel. Aprilaire recommends replacing it annually--so if you haven't replaced it recently, that would be the first step to take. Next, check the power supply to your Aprilaire unit. Turn the humidistat to 0%, and then turn it slowly back toward 35% until you hear a click at the unit. If you don't hear a click, you'll want to check that the unit is in fact getting electric power (you may want to get an electrician or furnace tech to do this). If you do hear the click, the next thing to check is whether you have sufficient water flow to your Aprilaire unit. On mine, I had to adjust my water supply saddle valve, as well as the inline valve on the discharge side of the solenoid (see prior post from this morning)--and this seemed to clear the lines and restore water flow. Once you achieve proper water flow, you will probably want to set your humidistat at 35% for winter temps of around 20 degrees F--but be sure to adjust it downward for colder weather. Comments, anyone?
Dec 13, 2008 |
Aprilaire 700 Humidifier