Question about Ruud UBHC Air Conditioner
I can't get my furnace to ignite and don't know what to check. It was a used furnace so I hav no manual
Again is this a spark or a glow coil? If it is a glow coil look at the coil and see if there is a crack or white spot on it. If so it needs to be replaced.
Posted on Jan 18, 2009
Coming from the induced draft motor is an orange or gray rubber tube leading to a switch pull the end off that is connected to motor and poke a wire or something to insure the hole is not blocked if it is not replace the hose. next step is to check the switch make sure if possible try to jumper 2 wires and turn unit back on if it works then either switch is bad or vent piping is blocked.. For your extreme Safety, Please Do Use Furnace in this condition until problem is fixed. thanks glad i could help
Posted on Jan 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2017 | Heating & Cooling
Jan 07, 2017 | Heating & Cooling
Jan 04, 2017 | Heating & Cooling
Jan 03, 2017 | Coleman Heating & Cooling
Jan 03, 2017 | Royal Heating & Cooling
Dec 18, 2016 | Heating & Cooling
Dec 25, 2014 | Heating & Cooling
Nov 07, 2014 | Heating & Cooling
3,044 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: