Question about Cadet Manufacturing 67507 Heater
I have a home with Cadet baseboard heaters. One has stopped working. The manual suggested checking wires, which are all connected and wired correctly. It then says that the limit may be defective and to replace it.
Where is the limit, how do I determine if it's defective, and how do I replace it?
First... did this heater work properly in the past?? if not, the wiring may be incorrect..... but to answer your question the safety limit is usually on the left end of the baseboard (inside the small cover). it is the round thing that is installed inline on the wiring. replacing it is an easy fix... just be sure to turn off the electric power FIRST.
Posted on Sep 29, 2009
The limit is a safety switch inside the unit to keep it from overheating if the fan doesn't turn on and is located inside the unit with what should be only 2 wires ran to it. you can determine if it is fauly by putting the leads of a multimeter while in the continuity mode, onto each lead of the switch, if the meter does not beep when this is done then it means that this switch is stuck in the open position and simply needs replacing. because it should automatically reset itself when it cools down.
Posted on Jan 24, 2010
Tips for a great answer:
Sep 01, 2014 | Cadet Manufacturing CADET Softheat...
Dec 12, 2013 | Heaters
Feb 13, 2011 | Cadet Manufacturing EBHA1000W The EBHA...
Jul 13, 2010 | Cadet Manufacturing 6F1500W Baseboard...
Mar 08, 2010 | Cadet Manufacturing CADET Softheat...
Apr 22, 2009 | Cadet Manufacturing CADET Softheat...
Mar 19, 2009 | Cadet Manufacturing 6F1500W Baseboard...
Feb 11, 2009 | Cadet Manufacturing 09954 Baseboard Heater
Feb 09, 2009 | Honeywell HZ517 Baseboard Heater
Mar 25, 2008 | Cadet Manufacturing 09950 Baseboard Heater
1,076 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: