Question about Heating & Cooling
The pilot light works just fine and the furnace starts up but then shuts off immediately. It keeps trying to start but the same thing keeps happening. Then out of the blue the furnace will work just fine!?!?!
If you have a hot surface igniter (glow coil) it has a secondary purpose after ignition and that is to sense that there is actually flame present. If the HSI is located on one end of the burners look to the other and see if there is a small rod that protrudes in to the flame as well. If so it is part of this flame proving cycle. Take some sand cloth and clean it. This may buy some time but the rod should soon bee replaced.
Posted on Jan 17, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 28, 2017 | Heating & Cooling
Sep 14, 2014 | Heating & Cooling
Apr 13, 2014 | Keystone 2013 Hideout 32FLTS
Nov 04, 2013 | Carrier Weathermaker 8000 Gas Furnace 125k...
Jan 13, 2010 | Heating & Cooling
Jan 10, 2010 | Dayton Gas Furnace Heater
Jan 01, 2010 | Heating & Cooling
Oct 08, 2009 | Heating & Cooling
Jan 06, 2009 | Heating & Cooling
Nov 08, 2008 | Cozy (W352E) Heater
Jan 21, 2018 | Heating & Cooling
Jan 21, 2018 | Dometic Heating & Cooling
154 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: