Question about Honeywell Programmable Thermostat Heater
TEMP SET 68/' ONLY RISES TO 61"/ .. BURNERS FIRES GOOD FULL FLAME BUT SHUT OFF ,BACK TO PILOT STAGE JUST AFTER 2 MINUTES ..THEN COMES ON AGAIN IN ABOUT 3-5 MIN...EQUIPPED W/ TWO STAGE FAN ...WHICH BLOWS LOW CONSTANTLY, HOWEVER IT DOES BLOW HIGH COOL AIR FOR A COUPLES MIN. AND THEN .. FULL FLAME AGAIN ......
It sounds like you have a dirty or faulty flame sensor im assuming that you have inshot burners in your furnace the flame sensor will be on the right or the left of the burner assembly opposite the pilot and ignitor it slip through the burner assembly and attaches to the burner it is l shaped steel that is fitted in a porcelin housing and when installed correctly it will be directly in front of one of the inshot burners when the main burner lites the flame touches the sensor and holds the gas valve open until the thermostat is satisfied remove it and sand the the l shaped metal end with 100 grit sandpaper until its clean and shinney then reinstall set thermostat to heat and see if it will stay lit if not get furnace brand model and serial# go to local hvac parts house and pick a new flame sensor if its a rheem i generally pay about ten dollars each my cost chances are cleaning will take care of the problem. good luck! hvac ike
Posted on Jan 20, 2009
I would check furnace filter first. If that looks good i would check the thermostat. To check thermostat turn power off to furnace then take thermostat off the wall and connect wires labbled R & W together then turn power on and check furnace to see if it runs for more than a couple of minutes. If so install a new thermostat. If that doesn't work let me know and i can give you a couple more thing to try.
Posted on Jan 18, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 10, 2017 | Heating & Cooling
Nov 08, 2012 | Heating & Cooling
Dec 31, 2017 | Goodman GMS90703BXA Heater
Oct 15, 2010 | Heating & Cooling
Mar 07, 2010 | Honeywell Programmable Thermostat Heater
Jan 18, 2010 | Honeywell Programmable Thermostat Heater
Dec 05, 2009 | Dayton (3E407) Heater
Feb 15, 2009 | Goodman GMS90703BXA Heater
Jan 17, 2009 | Honeywell Programmable Thermostat Heater
Jan 06, 2009 | Heating & Cooling
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
323 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: