Question about Heating & Cooling
We just replaced the inducer blower motor unit on above model. Then water kept getting trapped in the pressure switch tube, which the repair man came out and put the pressure switch up higher, everything was working well until this morning. You can hear the blower motor running, and the air going through, but he furnace wont kick on and run. What else could be going on?
Water should never reach the nipple for the pressure switch tubing on the IDM. Check the entire condensate drain system for obstructions. Verify water makes it from the furnace location to the outside drain. Flush p-traps and any anti-siphon devices thoroughly.
Posted on Apr 07, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Oct 22, 2016 | Amana Heating & Cooling
Nov 06, 2015 | Kitchen Ranges
Oct 23, 2013 | Coleman Intertherm Nordyne Miller Furnace...
Jan 28, 2010 | Heating & Cooling
Dec 13, 2009 | Amana PTC074B25AE Electric Heat Air...
Nov 28, 2009 | Heating & Cooling
Nov 25, 2008 | Amana Heating & Cooling
Apr 24, 2017 | Heating & Cooling
562 people viewed this question
Usually answered in minutes!