Question about Aprilaire 700 Humidifier
I have an Aprilaire 760 attached to my furnace, but it just started to leak quite a bit of water from the bottom of the unit. It leaked a considerable amount of water before I noticed the problem. I have since unplugged the humidifier and it seems to have stopped the dripping. Is there a solution you could recommend, or should I just leave it unplugged? Thanks for any help...
The tune up kit that I ordered arrived on Friday and I installed most of it on Friday night. While it is nice to have a new frame and the distribution panel and I think the price of the whole kit was fair considering it comes with the parts and 2 water panels, the fix was really simple.
The kit came with the water distribution tube with with a new blue orifice (Aprilaire #4232) already inserted. This orifice is in the end of the plastic tube at the solenoid end. When I removed the old water distribution tube, the old orifice was not really dark blue anymore but kind of a light blue and was deteriorating from 12 years of exposure to the chemicals in the water. What should have been a pin-hole size opening in the orifice was up to about 2mm or a little more so the orifice was letting way too much water through.
If anyone else has this leaking problem, and your orifice is several years old, I would check that first. It is a $2.75 part and may be the cause of the leak. The whole feed tube kit is only $8.75 and includes the feed tube, nozzle, orifice, ferule, compression nut, strainer so if you need to replace the orifice, I would order the whole feed tube kit for a little bit more.
Hope this helps,
Posted on Feb 03, 2009
After shutting down my 760 for the summer, I recently turned it on and it started leaking water from the bottom.. This is the first time I've had this problem. The unit is several years old and I average a filter change every two years. I took the unit apart and made sure all the drain components were secure in their proper discharges. This fixed some of the problem. I then noticed that the fan housing was not aligned all the way with the housing on the furnace. After correcting this, no leaks.
Posted on Feb 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 19, 2011 | Aprilaire 700 Humidifier
Oct 25, 2010 | Aprilaire 700 Humidifier
Feb 10, 2009 | Aprilaire 700 Humidifier
Jan 28, 2009 | Aprilaire 700 Humidifier
Dec 14, 2008 | Aprilaire 550 Humidifier
Jan 03, 2008 | Aprilaire 700 Humidifier
Dec 27, 2007 | Aprilaire 700 Humidifier
632 people viewed this question
Usually answered in minutes!