Question about Desa International GWP20T GLOWARM Wall Mounted Panel Heater
We have a model#CBN20T wall mount natural gas heater we can get the pilot light to light but as soon as we let up on the temperature selection knob we hear a click and the pilot goes out. We have occasionally been able to get the heater to stay lit for several hours - then it clicks and goes out.
Sounds like the thermocouple is going out this is the part the flame from the pilot burns on and tells the gas valve to stay open by producing a small amount of electrical current in milli-amps these can be purchased @ a good hardware store and you must position as it is when it comes out , and must be the same length , make sure to connect to gas valve clean and tight , also is there a moisture trap in the line if so you might need to turn off gas and make sure it is free of moisture , this is a good place to start with these items
Posted on Jan 17, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 24, 2011 | Vulcan Heating & Cooling
Jan 20, 2011 | Heating & Cooling
Dec 13, 2010 | Mr. Heater MH25NG InfraRed Gas Wall...
Nov 02, 2010 | Williams 3003622 Ceramic Wall Mounted...
Nov 06, 2009 | Desa International CBN20T Heater
Jul 16, 2009 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 16, 2008 | Dyna-Glo D-E37 Wall Mounted Panel Heater
168 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: