Question about Honeywell CT87B ROUND HEATING&COOLING MECHANICAL THERMOSTAT - WHITE Heater
Three electric baseboard heats w/single thermostat, trips main breaker when flipped on ? help why is this happening
I had this problem once in an apartment I own. it was an EXTREMELY ease fix. my problem as that the set screws in the breakers were not tightened enough, and would cause heat to build up, and trip the breakers. so..... first try to tighten the set screws on your breakers.
Posted on Sep 29, 2009
Your load from the heaters is too great for the wire and breaker installed. Add up the wattage of the heaters and divide the answer by whatever voltage the heaters are and that will give you your draw in amps if this number is higher than 80 percent of the breaker rating then this is against code and wire and breker need to be upgraded.
Posted on Jan 24, 2010
The three heaters are too much load for the circut breaker that they are on !Are they all on one breaker or fuse? if so you may have to use seperate breakers for all heaters!
I hope this was of big help!
Posted on Jan 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 14, 2014 | Cadet Heater. Soft Heat 71 in. 1,250-Watt...
Oct 01, 2014 | Honeywell Heating & Cooling
Jan 01, 2012 | Marley Electric Hydronic Baseboard Heater,...
Feb 18, 2011 | Honeywell (CT62B1015) Baseboard Heater
May 17, 2010 | Fahrenheat Electric Hydronic Baseboard...
Dec 16, 2009 | Honeywell Heat/Cool Thermostat
Feb 01, 2009 | Honeywell Programmable Thermostat Heater
Jan 26, 2009 | Honeywell Programmable Thermostat Heater
Dec 01, 2013 | Honeywell CT87B ROUND HEATING&COOLING...
327 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: