Question about Air Conditioners
Boiler fires up and temp at 82 degres d2 code appears but no heat to the rads
The boiler is airlocked.
Posted on Jan 26, 2009
Sticking diverter valve
Posted on Jun 28, 2009
The heat is obviously not getting away from the boiler due to either a blockage or more likely a closed valve. check that the flow and return valves are opened as some people accidently turn the return off when putting pressure in the boiler. if these are open then it is likely that the diverter valve is sticking. you can sometimes get them going temporarily by stripping them down or a persuasive tap on the motor but will stick again. will need replacing if this is the case. i can get hold of the diverters if you require one so post a reply if you do and i will give you my details.
Posted on Feb 07, 2010
I need ferroli optx 25 manuel please could anybody help thnks
Posted on Mar 07, 2013
Room stat is not calling for heat on ferroli optimax 31c
Posted on Jul 19, 2009
Tips for a great answer:
Dec 22, 2010 | Air Conditioners
Dec 18, 2010 | Air Conditioners
Dec 02, 2010 | Air Conditioners
Nov 28, 2010 | Quasar HQ2051TH Air Conditioner
Sep 26, 2010 | Quasar HQ2051TH Air Conditioner
May 20, 2010 | Quasar HQ2051TH Air Conditioner
Oct 07, 2009 | Comfort-Aire RAD-243 Air Conditioner
Mar 28, 2009 | Quasar HQ2051TH Air Conditioner
3,808 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: