Question about Heating & Cooling
Boiler fires up and temp at 82 degres d2 code appears but no heat to the rads
The boiler is airlocked.
Posted on Jan 26, 2009
Sticking diverter valve
Posted on Jun 28, 2009
The heat is obviously not getting away from the boiler due to either a blockage or more likely a closed valve. check that the flow and return valves are opened as some people accidently turn the return off when putting pressure in the boiler. if these are open then it is likely that the diverter valve is sticking. you can sometimes get them going temporarily by stripping them down or a persuasive tap on the motor but will stick again. will need replacing if this is the case. i can get hold of the diverters if you require one so post a reply if you do and i will give you my details.
Posted on Feb 07, 2010
I need ferroli optx 25 manuel please could anybody help thnks
Posted on Mar 07, 2013
Room stat is not calling for heat on ferroli optimax 31c
Posted on Jul 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2017 | Heating & Cooling
Jan 09, 2017 | Heating & Cooling
Jan 03, 2017 | Heating & Cooling
Jan 02, 2017 | Heating & Cooling
Jan 31, 2015 | Heating & Cooling
Jan 21, 2015 | Heating & Cooling
Jan 08, 2015 | Heating & Cooling
Jan 04, 2015 | Heating & Cooling
Jun 23, 2014 | Heating & Cooling
3,812 people viewed this question
Usually answered in minutes!