Question about Hoshizaki Freezer Commercial Ice Machines - KM900MRH Commercial Ice Machine
I have a Hoshizaki Modular ccrescent cuber Model KM-900MRH3 which is designed to have a remote condensor. My question is how far can the condensor be located away from ice machine?
Their web site has all your answers. Their tech support line is worth the wait. 1-800-233-1940.
I usually don't exceed 25 feet. If it is a straight up install, that is, the remote is on a roof, you may have to install traps to ensure proper oil return to the compressor, Otherwise, it will lockup on ya.
Posted on Feb 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 14, 2014 | Hoshizaki Commercial Freezer KM-500MAH
Aug 03, 2010 | Hoshizaki Commercial Freezer KM-900MRH3
Aug 02, 2010 | Hoshizaki Freezer Commercial Ice Machines...
Jun 05, 2010 | Hoshizaki Freezer Commercial Ice Machines...
Feb 06, 2010 | Hoshizaki Commercial Freezer KM-500MAH
Nov 19, 2009 | Hoshizaki Freezer Commercial Ice Machines...
Jun 28, 2009 | Hoshizaki Freezer Commercial Ice Machines...
Jul 30, 2008 | Hoshizaki Freezer Commercial Ice Machines...
Jul 02, 2008 | Hoshizaki Commercial Freezer KM-500MAH
84 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: