Question about Heating & Cooling
On,unit was working,unit would cut off with thermostat,kids started cutting it off with main breaker,now willnot work at all?
You probably have a bad breaker.
Check to see if you have 220 volts coming into the breaker. (while the breaker is in the ON position) and check to see if there is 220V coming out of the breaker. If no, then you have a bad breaker.
If you do, let us know and we can help you diagnose from there.
Posted on Jan 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 24, 2015 | Heating & Cooling
Jan 31, 2015 | Heating & Cooling
How do you know power is at the outdoor unit? Did you check it with a meter? Check your breaker. If there's power at the outdoor unit, then shut the power and test your contacter. If the contacter has supply power then check the low voltage (24-28 volts) that operates the contacter, and if none check the low pressure cut-out,high pressure cut-out and make sure the thermostat is calling for cool. All ok so far, then test your capacitor. I forgot to mention to check for loose, broken, and disconnected wires.
Aug 24, 2013 | Carrier Heating & Cooling
Apr 07, 2017 | Heating & Cooling
Aug 22, 2011 | Dryers
Feb 10, 2011 | Whirlpool LER4634J Electric Dryer
Dec 07, 2010 | Crosley CAE12ESR Air Conditioner
Sep 24, 2010 | Hamilton Beach Water Cooler with Storage...
Mar 26, 2010 | Dometic Rooftop RV Air Conditioner
Jan 04, 2010 | Honeywell Power Humidifier: Furnace...
51 people viewed this question
Usually answered in minutes!