Question about RELIANCE ELECTRIC WATER HEATER
Woke up with no hot water, but could hear water in the water pipes(a natural occurance in this older house-=when the water is running) replaced the heating elements, high temp cut off, and the upper thermostat. we briefly have hot water, but can still hear water flowing through the pipes, even when there is no water running. could this be a fault in the hot water heater-allowing water to seep through, or is it a fact that we have a leak in the walls? the hot water heater we are dealing with is 15 yrs old at least.
(my e-mail address has zeroes instead of o's)
Before you can assume you have a problem with the hot water heater you need to find the leak first. If you indeed have a leak you are not only loosing water, but your hot water heater may being trying to heat the tank all the time.
I suggest that you get some help from a friend, First start off by making sure all faucets and toliet valves are turned off. Try to locate the sound of the running water. Now place you help new the sound and go turn off the water to the hot water heater, Have your friend tell you if the water sound stops. IF the water sound stops than this is a leak in a pipe and it is a hot water leak. In this case you will need to turn off the power to the hot water heater or the gas supply.
By leaving the power or gas to the water heater you are mearly tossing cash out the window because the water heater can not heat the amount of water traveling through it.
You will then need to try to find access to the pipe that is leaking, either through removing drywall, hopefully it's in a place that can be accessed easily, but either way you have to repair the leak.
If you have copper lines in the house or Sea tek (plastic lines) you should be able to purchase either soldier copper fittings and some soldier or some plastic couplings to make the repair.
If by chance you have a real old house that is using galvanized pipe you may have a bit harder project in having to remove the old pipe back to the nearest joint..
If you are familiar with soldiring copper pipes than you should have a issue. however because of the relative placement of the leak sounds to be in a wall you might consider finding the leak and calling a plumber or a good friend that has a good deal of plumbing experience to help.
Posted on Oct 18, 2013
That may be normal, sometimes the heater may be pumping water into the heating system to keep pressure level.
Posted on Jan 23, 2009
Yes, I'd say you have a leak somewhere.
Do you have a home heater that uses the hot water for its source of heat?
If your dip tube is broken it could also contribute to running out of hot water quickly or near emediatly.
The dip tube is what forces the water to come off the bottom of the tank instead of the top where the cold comes in. If the tube is failed, then you are just recycling cold water and not touching the hot water below it.
But if water is flowing through the pipes and nothing is turned on with no water based heater, then you must have a leak somewhere.
Posted on Jan 16, 2009
Welcome to Fixya! You need to Replace that Hot Water Heater. After this is Done Hopefully, You will not here the Water inside the Walls. Either way the Water Heater is Bad. Could STILL be a Leak in the Wall though! Make sure and check!
Posted on Jan 16, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 29, 2014 | Water Heaters
May 04, 2013 | Rheem Water Heaters
Aug 28, 2012 | Reliance 606 Series 40 Gallon Electric...
May 11, 2012 | Rinnai Water Heaters
May 15, 2011 | Rheem Water Heaters
Dec 17, 2010 | Laing Thermotech Autocirc Undersink...
Feb 08, 2010 | Noritz 7.1 Gpm Natural Ng Gas Tankless Hot...
Oct 02, 2009 | Rheem Water Heaters
Mar 17, 2009 | Rheem 50 Gallon FVR NATGAS Water Heater...
46 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: