Question about Rheem Tankless Hot Water Heater Rtg-74pvp-2 7.4 Gpm
I have a richmond rmtg-74pvn and I have a problem with the cold down draft is blowing down the vent and freezing the water in the heating tubes.the damper in the top of the unit is functioning properly.
I HAD THE SAME PROBLEM ON 2 OF THESE. I CALLED THE COMPANY AND THEY SENT ME A COMPLETE NEW VENT KIT WITH A DAMPER AT THE OUTSIDE WALL. HAVE HAD NO TROUBLE SINCE INSTALLING
Posted on Jan 25, 2010
I got a dryer vent kit (Alum) took the extension pipe off and cut the center hole open a little and slid it over the existing elbow. Now when the heater turns on the little flap opens and when the air flow stops the flap closes stopping the air coming down the pipe.
Posted on Jan 16, 2009
Install a backdraft damper which is like a check valve for vents. Make sure you use only Category III products.
Posted on Jun 10, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 05, 2015 | Water Water Heaters
Jul 02, 2014 | Rheem Paloma Tankless Water Heaters...
Oct 14, 2013 | Water Heaters
Dec 28, 2012 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Dec 02, 2012 | Water Heaters
Mar 27, 2011 | Rheem Paloma Tankless Water Heaters...
Mar 05, 2011 | Rheem RTG-53DVN Direct Vent Natural Gas...
Aug 22, 2010 | Rheem Paloma Tankless Water Heaters...
May 16, 2010 | Rheem Tankless Hot Water Heater...
Jan 16, 2009 | Rheem Tankless Hot Water Heater...
323 people viewed this question
Usually answered in minutes!