Question about Heating & Cooling
I have a Rheem Classic 80 furnace that would ignite but not stay lit. Cleaned the ignition sensor which was easy to get to and the flame sensor which was under the burner plate and it fired up and stayed lit. The flame sensor was about 6" under the burner plate. Easy to get out, but tough to get back in. Used the old piece of paper shim trick to get the screw to "stick" in the socket and it was much easier to position the screw and get it back where it belonged.
Posted on Jan 16, 2015
Sounds like you may have a bad thermocouple. Little unit/sensor at the pilot flame that reads the pilot light is on so that the gas will flow.Usually has a coiled small copper tube.
Posted on Jan 17, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 07, 2015 | Heating & Cooling
Oct 25, 2013 | Rheem Gas Furnace 125,000 BTU 80 AFUE....
Jan 30, 2011 | Heating & Cooling
May 23, 2010 | Heating & Cooling
Jan 10, 2010 | Heating & Cooling
Jan 31, 2009 | Heating & Cooling
Dec 23, 2008 | Heating & Cooling
Oct 20, 2008 | Ruud Heating & Cooling
403 people viewed this question
Usually answered in minutes!