Question about Fedders Y Chassis A6Y18F7A Air Conditioner
Water used to drip from the outside of our Fedders unit properly, but not for past 2 summers. Also, the unit cools the air well, but the room feels damp, humid. It is as if the air is being cooled but just not quite enough for the condensation temperature to be reached (ie, 100% rel.humidity), and, thus, condensation does not occur. Either that or somehow the condensed water is being reabsorbed by the cooled air. The unit is tilted to the outside properly (about 2-degrees down to outside), and there is no water running into the room. Any suggestions? Thanks.
HELLO .. HOPEFULLY YOUR UNIT SLIDES OUT OF THE A/C HOUSING, IF IT DOES REMOVE IT. (THERE MAY BE A FEW SCREWS HOLDING IT IN PLACE USUALLY BEHIND THE FRONT GRILL) PUT DOWN SOME OLD RUGS FIRST AND HAVE SOMEONE HELP YOU SLIDE IT OUT. GET OT THE GARDEN HOSE AND SPRAY NOZZLE. PROP UP THE FRONT OF THE UNIT SO IT DRAINS TO THE REAR. BOTH THE EVAPORATOR COIL AND CONDENSER COILS SHOULD BE CLEAN. YOU WILL NOT SEE DIRT ON THE OUT-SIDE OF THE COIL ... IT WILL BE ON THE INSIDE HIDDEN BY THE CONDENSER FAN BLADE. BE VERY CAREFUL NOT TO BEND THE FAN BLADE WHILE INSPECTING OR WASHING. BE EXTREAMLY CAREFUL TO COVER THE MOTOR AND ELECTRICAL CONTROL BOX WITH PLASTIC BAGS TO ENSURE ALL ELECTRICAL COMPONENTS STAY DRY. FACTOID: 90% OF AIR CONDITIONERS THAT "DONT COOL AS WELL ANYMORE" IS DUE TO DIRTY COILS. THERE IS ALSO A TUBE OR CHANEL THAT DRAINS THE WATER FROM THE EVAP (FRONT) COIL TO THE BACK OF THE UNIT. THAT CONDENSATE WATER IS SUPPOSED TO ACCUMILATE IN A SNALL RESEVOIUR WHERE THE SLINGER RING ON THE OUT SIDE COIL FAN BLADE PICKS IT UP AND HELPS COOL THE HOT CONDENSER COIL. SOME OLDER UNITS MAY NOT HAVE A SLINGER RING AROUND THE OUTSIDE OF THE BLADE. NOW ... MAKE SURE YOUR OUTSIDE FAN BLADE IS CLEAN. AS WELL AS THE INSIDE BLOWER FINS ON THE "SQUIREL CAGE". NOW THAT YOUR UNIT IS CLEAN AND YOU CAN SEE CLEARLY THROUGH BOYH COILS, GO AHEAD AND OIL YOUR MOTOR. CHECK TO SEE IF YOUR FAN MOTOR HAS "OIL CAPS" USUALLY THEY ARE AT THE TOP OF THE 2 ENDS OF THE MOTOR. IF THERE ARE CAPS REMOVE THEM AND USE A STRAIGHT WEIGHT (NON-DETERGENT OIL). SOME WINDOW A/C'S UNDER 12,000 BTU'S ARE SEALED UNITS. IN THAT CASE YOU WILL HAVE TO REMOVE THE UNIT FROM THE WINDOW MOUNTING BRACKET. AND FOLLOW THE SAME PROCEEDURE AS LISTED ABOVE. GOOD LUCK AND STAY DRY.
Posted on Jun 25, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2017 | Heating & Cooling
Aug 28, 2012 | Frigidaire FAH124N2T Air Conditioner
Jul 06, 2011 | Fedders A6P09S2A Air Conditioner
Jun 04, 2011 | Frigidaire Heating & Cooling
May 04, 2011 | Mitsubishi MS09TW Air Conditioner
Aug 20, 2010 | Fedders A6D24E7D Wall/Window Air...
Aug 05, 2010 | Frigidaire FAC124 wall/Window Air...
Jun 14, 2010 | Fedders A6X05F2G Wall/Window Air...
Aug 01, 2009 | Fedders AEQ07F2BG Air Conditioner
Jul 19, 2009 | Fedders Heating & Cooling
Jan 23, 2019 | Heating & Cooling
270 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: