Question about Ruud Heating & Cooling
"There is water coming from the bottom of the panel that is removable by that pipe. Not the pipe for overflow of the tray beneath the unit. I had trouble reading the model #.
Cant understand what you are describing. is the drain pipe clear. water coming out end into french drain or pump. if not clear out by mechanical means or by blowing.
Posted on Jan 15, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 06, 2017 | Electrical Supplies
Jul 12, 2013 | GE J Series 20.6 cu. ft. Top Freezer...
am a certified HVAC Technician. I have worked in the field since 1996. I have
seen this hundreds of times, if not a thousand times, in the past. Every
central air conditioning and heat pump system comes with TWO drain pans, The
MAIN drain pan is located within the AIR HANDLER (blower) UNIT, while the
EMERGENCY DRAIN PAN is extremely LARGE and sits under the ENTIRE AIR HANDLER
(blower) UNIT. The ONLY time water will be INSIDE an EMERGENCY DRAIN PAN is
when the MAIN DRAIN PAN condensate drain line is CLOGGED, causing the MAIN
DRAIN PAN to overflow. What causes the drains pans OR the drain lines to become
clogged is slime and scale from the condensate water as well as debris from
within the attic that may have either been blown by the air or may have simply
have fallen into the emergency drain pan; or some insects from the out of doors
have traveled up into the PVC Drain line and built a nest on the downward side
of the P-trap. The P-trap is designed to prevent critters from entering your
home through the PVC drain lines. Most CLOGS occur at the P-TRAP location.
The BEST thing to do is:
Locate the WHITE PVC drain pipe outside your house and ensure there is NO water
draining from it.
2. Locate the same WHITE PVC drain pipe inside your house. You should notice a "TEE" where two WHITE PVC drain pipes merge into ONE WHITE PVC drain pipe.
the below steps, in the order shown:
A. FIRST, find another person to act as your second set of eyes at the end of the WHITE PVC Drain Line that is located outside of your home. That person will be looking for water or debris to EXIT the end of that WHITE PVC DRAIN LINE.
SECONDLY, locate the WHITE PVC "P-TRAP" inside your house. It is
normally located within a couple to three feet of your indoor air handing
C. THIRDLY, very gently lift the entire WHITE PVC drain line up in the air as high as you can without breaking it, and slam it down onto the rafters or attic floor or garage floor. You are attempting to dislodge the CLOG within the drain pipe WITHOUT having to actually CUT the PVC and without damaging or breaking the WHITE PVC. Depending on how old the system is, it may or may not be brittle; and it may not take much to damage or break the PVC, which will cause leaks. So, be very careful at this point.
Ask the person outside if anything has started to EXIT. You can ALSO usually
hear water start to drain if you put your ear up to the drain line. If the
person said "NO"and if you don't see the water level getting LOWER in the
EMERGENCY drain pan, then REPEAT step "C" above.
If the person informs you that there IS water now starting to exit the WHITE
PVC DRAIN PIPE, you should then wait until all water has drained from the
EMERGENCY DRAIN PAN; and then pour at least 1 quart of BLEACH down that drain,
from the EMERGENCY DRAIN PAN exit. The BLEACH will further clear out any SLIME
which may be remaining within the "P-TRAP" and will also CLEAN OUT and
DISINFECT that drain line.
If the above steps do NOT work for you, then prepare to go into the next LOGICAL phase of your attack. Please NOTE: I am limited to 10,000 characters in my response, so I'll repost additional STEPS in another RESPONSE. Good Luck!!!
Sep 05, 2012 | Goodman CLQ36AR49 Air Conditioner
Jul 29, 2011 | Carrier 38CKC042 Air Conditioner
May 08, 2010 | Weather King 12AJA4201AH Air Conditioner
Jan 24, 2010 | General Filters 1042-LH Humidifier
Nov 14, 2009 | Heating & Cooling
Nov 09, 2009 | Heating & Cooling
Jul 13, 2009 | Heating & Cooling
Jan 21, 2009 | Heating & Cooling
118 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: