Question about Belkin Universal UPS UPS System
I have a Belkin F6C120-UNV. The symptom is that there is no power from the battery backed outlets. There are also no indicator leds on. When the unit is unplugged and I press the power-on button for several seconds I get a quick beep and the "ON Battery" led flashes very briefly. I have left the unit charging with no load for several days with no change. I opened the case to measure battery voltages and measured 8 volts on one and .4 volts on the other. I'm sure these voltages indicate problems with the batteries, but would this also explain why none of the indicator leds are working? If the problem is most likely only the batteries I would probably replace them but if there's some other problem as well I'll probably scrap the unit. Can someone suggest other troubleshooting I should do? Is it worth trying to charge the batteries with a car battery charger? Other suggestions appreciated.
Very likely, "would this also explain why none of the indicator leds are working?"...the dead batteries are your problem. you can try this test, since you had it opened: 1.) disconnect internal batteries, label the wires by terminal location. 2.) connect (2) 12 volt car batteries to same exact wires that you just disconnected, noting correct polarity. 3.) power up UPS. if everything ok, then buy 2 replacement batteries for UPS. if not ok, buy new UPS after through search inside UPS reveals no blown fuses or other faults including poor wire connections.
Posted on Jun 17, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 26, 2013 | Belkin (F6C800-UNV-PL) UPS System
Jan 31, 2012 | Belkin (f6c900-unv) UPS System
Apr 05, 2011 | Power-Sonic Belkin 120Whr F6C900-UNV UPS...
Mar 14, 2011 | Belkin 900VA ( F6C900-UNV ) UPS System
Nov 25, 2009 | Belkin 900VA ( F6C900-UNV ) UPS System
Sep 22, 2009 | Belkin Enterprise (F6C1200-UNV)...
Dec 26, 2007 | Belkin ( F6C500-UNV) (Bundle)...
556 people viewed this question
Usually answered in minutes!