Question about Goodman CLQ36AR49 Air Conditioner
Added new board does the same thing. changed the tstat and checked the wiring still nothing. defrost tstat closed i just can't thing about a nother cause?
Is sensor at proper location? try turning sensor ? Ohm sensor as you turn it.
Posted on Jan 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 01, 2013 | Goodman Heating & Cooling
May 15, 2011 | Heating & Cooling
Apr 30, 2011 | Ruud UBHC Air Conditioner
Jan 28, 2011 | Heating & Cooling
Jan 23, 2010 | Ruud UBHC Air Conditioner
Dec 08, 2009 | Goodman CPLE24-1 Air Conditioner
Sep 11, 2009 | Goodman CKL36AR36 Air Conditioner
Jul 31, 2009 | Carrier 38BRC048 Air Conditioner
Apr 04, 2009 | Ruud UBHC Air Conditioner
53 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: