Question about Heating & Cooling
All the wires on the schematic are in correct places, but everytime i try to plug in the 220v cord it pops the 3amp fuse on the control board?
also the model # and serial# are scratched off
You have a short to ground somewhere in the low voltage wiring.
You will need an OHM meter to test each 24V component for continuity to ground.
Test each part with the wires disconnected. If all the parts are OK, then it is a wire touching somewhere. (unlikely but pssible)
I would start testing at the 24V side of the transformer. Often times it is the boad that has shorted internally.
Sometimes you can look at the back of the board and see burn marks where one circuit has shorted to another.
Contactor and relay coils are also known foir this problem. (24 V coils power the relay, sending high voltage to its corresponding component.)
Posted on Jan 14, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 17, 2012 | Goodman Heating & Cooling
Oct 18, 2011 | Goodman GMS90703BXA Heater
Sep 15, 2009 | Westinghouse WWS833ES Super Capacity Top...
Aug 18, 2009 | Goodman Heating & Cooling
Jun 21, 2009 | Goodman Heating & Cooling
Oct 21, 2008 | Goodman CLQ36AR49 Air Conditioner
Sep 21, 2008 | Goodman Heating & Cooling
301 people viewed this question
Usually answered in minutes!