Question about SySTOR Systems (400S52) Burner
I have a Riello 40 burner. I had oil delivered this past sunday. The burner was working fine until the oil delivery(may be a coincidence.) When the house got a little cool I checked and the burner had the orange light on indicating that it had tripped out. I hit the reset button and the burner started up again. I had to do this several times during the day. The burner ran all day monday without a problem but the problem occured again on tuesday. I was finally able to restart it again at 2:17 am on wednesday mornign. Again it ran for several hours before tripping out again. During this situation it took mulltiple hits on the reset button and it still keeps tripping out. Normally even if the tank runs dry it is easy to restart. Now it is almost impossible to start.
They could have disturbed the sludge in the tank when refilling. If you do not have a filter in place it may have clogged the pump or jet and making it hard to start. These need yearly maintenance anyway. The pumps usually have a screen inside and the jet has a screen inside. First,open the bleed on the pump and purge some oil from the line and see if it is flowing freely. If so, the take the drawer assembly out and clean it. Make sure the jet is clear, by blowing through the attached oil line. You should see/feel a fine mist of oil come out. Electrodes should be about 5/32" apart for an F5.
Posted on Jan 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 21, 2014 | Honeywell Biasi B10-3 Boiler ,riello...
Sep 23, 2013 | Honeywell Biasi B10-3 Boiler ,riello...
Oct 05, 2012 | Honeywell Biasi B10-3 Boiler ,riello...
Feb 02, 2011 | Heating & Cooling
Sep 25, 2010 | Heating & Cooling
Apr 19, 2010 | Heating & Cooling
Nov 28, 2009 | SySTOR Systems (400S52) Burner
Jan 19, 2009 | Heating & Cooling
Dec 27, 2008 | Heating & Cooling
690 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: