Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
GOto the iside unit itself. and remove the door and look for a terminial strip that the thermostat wires from the thermostat connects to and write down the colors wires and the letters they're connected to and connect the same to the thermostat .... they should be... r--red=power w-white=heat y--yellow=cool g-- green=fan! See which wires/ colors they're not using and bend back! Thank-you-very-much!
Posted on Sep 01, 2008
a. Remove the cover of the thermostat.
b. Connect the RED wire from the air conditioner
to the RC terminal on the thermostat.
c. Connect the YELLOW wire from the air conditioner
to the Y terminal on the thermostat.
d. Connect the BLUE wire from the air conditioner
to the H terminal on the thermostat.
e. Connect the ORANGE wire from the air conditioner
to the G terminal on the thermostat.
f. Push the thermostat wires into hole in wall and
fill excess hole with insulation.
g. Mount thermostat base to the wall with screws
h. Check all thermostat wires on base to ensure
they are completely clear of the bimetal coil of
the thermostat. Adjust if necessary.
i. Replace thermostat cover.
If nothing operates on the air conditioner, remove the
return air grille assembly and verify the red, orange, yellow
and blue wires are properly connected (red-to-red,
Next, disconnect the red wires and check for 12 volt
DC between the red wire from roof section and the orange
or blue wire from roof section. If no voltage received,
refer to Section F2. If voltage is received, the
problem lies with the thermostat or thermostat wires.
Next, disconnect all 4 wires (red, orange, yellow and
blue) from the thermostat. With the thermostat set on
COOL mode, FAN mode set on AUTO and HIGH, and
temperature selector set lower than the room temperature. Check for continuity between terminal RC (red wire)
and terminal G (orange wire); and RC (red wire) and
terminal H (blue wire). If continuity is achieved on each,
proceed with the next step.
Set fan switch to LOW. Continuity should NOT be present
between terminal RC and Terminal H, but present between
the other terminals (Y & G) and terminal RC.
If all of the previous checks are good, the thermostat is
good, do not replace it. If any one of the previous checks
are not correct, replace the thermostat.
Posted on Jun 29, 2009
Hello,You forgot to wire the O terminal w1 witch is the reversing valve.It is important to check if old stat is using O or B in witch case B terminal=w1 leaving O unused.
Posted on Apr 21, 2010
Tips for a great answer:
Apr 21, 2013 | Filtrete Thermostat. 7-Day Digital...
Jun 21, 2011 | Heating & Cooling
Feb 22, 2011 | Honeywell CT87B ROUND HEATING&COOLING...
Dec 25, 2010 | JVC Car Audio & Video
Sep 20, 2010 | Heating & Cooling
Jun 27, 2010 | Heating & Cooling
Oct 20, 2009 | GE Zoneline AZ55H09D Air Conditioner
Sep 22, 2009 | Heating & Cooling
Jun 03, 2009 | Heating & Cooling
Mar 08, 2009 | Hunter Fan Company 5/1/1 Programmable...
28 people viewed this question
Usually answered in minutes!