Question about Heating & Cooling
Is the inducer motor running?
Posted on Dec 13, 2012
Check and make sure that you are getting 24v back on the white wire from the t'stat in the furnace. If yes than your problem is with the furnace. If no, your problem is with the thermostat. You need to establish where the problem is first.
Posted on Dec 13, 2012
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: the furnace will light up
First, for those of you who might not know, "What is a flame sensor?" A flame sensor is a safety device. When your furnace's main burners ignite (light Up) the flame sensor picks up the heat from the furnace's main burning and says, "YES," and sends a signal back to the main furnace control board saying that it is OK to let the main burner stay on. Or if the main burners do not ignite, the flame sensor does not pick up the heat and says, "NO" to the main control board, Shut That Gas Valve and Main Burners Down! Thank God we have safety controls like the flame sensor. Most of the time, after turning your furnace's power off, you may clean the flame sensors with light sand cloth, emery cloth or steel wool. Reinstall the flame sensor and you are back in business! Over the years flame sensors can build up a light coating of burned-in dust and dirt. This insulates the flame sensor so that it doesn't sense the heat of the flame well enough, so by cleaning it you have almost restored it to its new condition. Seldom, but sometimes they do go out completely.
Posted on Dec 08, 2010
Tips for a great answer:
Feb 04, 2018 | Gibson Heating & Cooling
Dec 30, 2014 | Heating & Cooling
Jan 27, 2014 | Goodman GMS90703BXA Heater
Dec 12, 2010 | Honeywell Heating & Cooling
Dec 08, 2010 | Coleman Heating & Cooling
Feb 07, 2010 | Goodman Heating & Cooling
Nov 23, 2009 | Heating & Cooling
Nov 12, 2009 | Honeywell Power Humidifier: Furnace...
Dec 21, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
33 people viewed this question
Usually answered in minutes!