Question about Pentair Easy Touch Indoor Control Panel for 8 Function Systems
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This is an ignition flame falure code. Could be you don't have gas getting to the pilot, no spark to ignite the pilot or your ignition is not reading the flame. Sorry to say but it's probally time to get the pool guy out to look at it. Good luck.
Posted on Apr 15, 2010
SOURCE: heater cycles on / off
This could be a water flo problem. you need to chech to be sure your by-pass valve is closed down enough to force water threw heater, There is a internal by-pass that could be a problem also, or a bad pressure switch. If the by-pass isn't the problem then you should check these also.
Posted on Jul 26, 2010
This reminds me of some of the High temp sensors ive replaced. I would start with checking the pumps flow to the heater. Make sure there are no abstructions and at least 35 GPM (gallons per minute) running to the heater. If your flow is too low, you will trip the high limit sensor after a short while.
This could also mean you need to clean out the heat exchanger. When an exchanger gets dirty, it blocks the flow of water, slowing it down and "super heating" itdue to the water being in contact with the exchanger for too long. This will also trip the high limit and call for service.
If both the above items check out, contact me @ email@example.com and I will guide you further.
Posted on Nov 23, 2010
If the Easy Touch is reading the correct temperature, but the heater is not - you need to double check the temperature of the pool water with a standard pool thermometer.
Other things to consider:
1) The water is traveling too slowly through the heater. If the water is heating too quickly, then it will shut it off. If it takes a while for this to occur, then this would not be the issue.
2) Thermostat/thermistor is incorrectly reading the temperature of the water prematurely shutting the system down.
Make sure you really are checking the temperature of the water and matching this temperature up with one of the two readings that you are getting. Don't just take the word of the displays on either unit.
Posted on Dec 10, 2010
SOURCE: Have a Pentair MasterTemp 400
Thank you for posting your question here on Fixya.com. If this answer does not fix your problem, please comment with additional details prior to rating the answer. You may also contact me thru our website at www.arrowpools.net. Positive feedback is appreciated once your problem is solved!
Error code E05 can be caused by many failures in several places. The owner's manual has a decent flow chart in it to help diagnose where the trouble lies. You will find it on page 43 here...
Identifying problems with an electronically controlled pool heater is not a job for most homeowners without training and/or experience with this type of equipment. If you are unsure how to proceed no amount of tips from a site like this will replace experience. You may want to consider hiring a professional to look at your heater.
If you decide to pursue the repairs and need additional support please post as specific a question as you can as a comment to this reply.
Thank you for posting your question here on Fixya.com.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. You may also contact me thru our website at www.arrowpools.net. Positive feedback is appreciated once your problem is solved!
Posted on Mar 30, 2011
Tips for a great answer:
May 15, 2014 | Pentair Mastertemp Heater
Apr 18, 2014 | Pentair Mastertemp Heater
Mar 27, 2011 | Pentair Easy Touch Indoor Control Panel...
Mar 04, 2017 | Pentair MasterTemp 400000 BTU Pool and Spa...
Dec 10, 2010 | Pentair Mastertemp Heater
Nov 23, 2010 | Pentair MASTER TEMP HEATER 400 000 BTU NG...
Oct 17, 2010 | Hayward Pool & Spa
Jun 07, 2014 | Pentair Easy Touch Indoor Control Panel...
62 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: