Question about Weather King 12AJA4801AH Air Conditioner
I posted a question about the unit having heating problems unless the temp outside was in the 50-60's. If the temp is lower the unit constantly runs and never gets to desired temp thermostat is set at. Upstairs (I have a 2 story) the heat comes out hot and has no problem reaching desired temp. We have other issues but this is a start! Please advise..
Model Number not found on site WSKA-A024JK 000
Hey kellyrepp -- Three things to check quickly, so many things can be wrong, but i will try to help with the info you gave me.
The first sounds like your electric aux heat is not wired in or not working correctly , this should kick in when the heat pump cannot keep up with desired set temperature. For sure thats a problem
The second thing i would check is that the compressor for that unit is running. It should sound exactly like the one for the upstairs, the fan noise should be like a whrrrr , and the compressor should be a semi loud hummm.
Third feel the pipes on the outside unit that are on the outside of the unit (the unit for the second floor) Let the unit run for 5 minuites. Now check that the first floor unit pipes are the same tempereture. They are about 110 degrees or so, depending on the outside temperatur , be carefull not to burn yourself. If the lower unit is colder , the two most prominent problems would be #1 the compressor is not running #2 Low on freon.
Hope that helps
Posted on Mar 06, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2015 | Emerson 1F89EZ-0251 Blue 2" Thermostat,...
Jan 15, 2011 | Heating & Cooling
Aug 17, 2010 | Weather King 10AJA6001AH Air Conditioner
Jan 12, 2010 | Carrier XQB101D Air Conditioner
Jan 11, 2010 | Weather King 12AJA4801AH Air Conditioner
Dec 03, 2008 | Heating & Cooling
Nov 25, 2008 | Honeywell TH4210D1005 Heater
Nov 24, 2008 | Weather King 12AJA4801AH Air Conditioner
313 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: