Question about Weather King 12AJA4801AH Air Conditioner
I posted a question about the unit having heating problems unless the temp outside was in the 50-60's. If the temp is lower the unit constantly runs and never gets to desired temp thermostat is set at. Upstairs (I have a 2 story) the heat comes out hot and has no problem reaching desired temp. We have other issues but this is a start! Please advise..
Model Number not found on site WSKA-A024JK 000
Hey kellyrepp -- Three things to check quickly, so many things can be wrong, but i will try to help with the info you gave me.
The first sounds like your electric aux heat is not wired in or not working correctly , this should kick in when the heat pump cannot keep up with desired set temperature. For sure thats a problem
The second thing i would check is that the compressor for that unit is running. It should sound exactly like the one for the upstairs, the fan noise should be like a whrrrr , and the compressor should be a semi loud hummm.
Third feel the pipes on the outside unit that are on the outside of the unit (the unit for the second floor) Let the unit run for 5 minuites. Now check that the first floor unit pipes are the same tempereture. They are about 110 degrees or so, depending on the outside temperatur , be carefull not to burn yourself. If the lower unit is colder , the two most prominent problems would be #1 the compressor is not running #2 Low on freon.
Hope that helps
Posted on Mar 06, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2015 | Emerson 1F89EZ-0251 Blue 2" Thermostat,...
Jan 15, 2011 | Heating & Cooling
Aug 17, 2010 | Weather King 10AJA6001AH Air Conditioner
Jan 12, 2010 | Carrier XQB101D Air Conditioner
Jan 11, 2010 | Weather King 12AJA4801AH Air Conditioner
Jan 12, 2009 | Weather King 12AJA4801AH Air Conditioner
Dec 03, 2008 | Heating & Cooling
Nov 24, 2008 | Weather King 12AJA4801AH Air Conditioner
304 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: