Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
-Start the unit.
-Press EMERGENCY OPERATION switch.3-minute time delay works.Test run operation operates for 30 minutes.
-Check voltage to terminal block of outdoor unit.Is there 12V DC between 2-1?
-If voltage is presenet check the wiring, compressor contactor outdoor fan motor and compressor.
-If no voltage check voltage to terminal block of indoor unit.Is there 12V DC between 2-1?
-If if voltage is present re-connect the continuity of indoor and outdoor unit connection.
-If no voltage replace the indoor electronic control P.C.
-But also check the coil thermistor sensor and room air thermistor if this two is out of range it can cause the tripping of out door unit. It has the resistance of 8 to 10 k ohms at 25 deg c temp.
Posted on Jan 08, 2008
With a heat pump system there are always going to be a back up heat strip inside the Air Handler.
If you detect a faint humming in the Condenser call your local service company and ask them to come and replace your capacitor in the condenser. The humming is from the contactor engaging but not being able to start the compressor due to not having the required Microfarads to start it.
Let me know if this helps
Posted on May 08, 2009
Check your filters, dog hair and lack of maintenance will definitely burden the cooling mode of the Mr Slim units.
Posted on Aug 24, 2009
Hi FixYa team. After about 2 hours on the internet I managed to find a PDF file of the operating manual for my air con.
Thankyou for your prompt response. I'll be using your services again!
Posted on Jan 14, 2010
Tips for a great answer:
Sep 09, 2016 | Heating & Cooling
Dec 19, 2015 | Fujitsu 9RLS 9000 BTU Split System Air...
Jul 26, 2015 | Heating & Cooling
Dec 26, 2010 | Samsung Heating & Cooling
Aug 25, 2009 | LG LS092CE Split System Air Conditioner
Aug 22, 2009 | Mitsubishi Heating & Cooling
May 07, 2009 | Heating & Cooling
Feb 16, 2009 | Cfm Daikin R410a Split System Air...
107 people viewed this question
Usually answered in minutes!