Question about Heating & Cooling
With a new thermostat installed the furnace will run the blower fan once in a while with the thermostat set in the off position and blower on auto. Would this be a bad board?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: furnace won't stay running
Furnace fails to operate.
• Integrated control module
diagnostic LED is
flashing ONE (1) flash.
• Furnace lockout due
to an excessive
number of ignition
“retries” (3 total)1.
• Failure to establish flame.
Cause may be no gas to
burners, front cover
pressure switch stuck open,
bad igniter or igniter
alignment, improper orifices,
or coated/oxidized or
improperly connected flame
• Loss of flame after establishment.
Cause may be
interrupted gas supply, lazy
burner flames (improper gas
pressure or restriction in flue
and/or combustion air
piping), front cover pressure
switch opening, or improper
induced draft blower
• Locate and correct gas
• Check front cover
operation (hose, wiring,
Correct if necessary.
• Replace or realign
• Check flame sense
signal. Sand sensor if
coated and/or oxidized.
• Check flue piping for
length, elbows, and
• Verify proper induced
draft blower performance.
Posted on Nov 25, 2008
When you call for fan in auto ensure your getting 24 volts at pin on control board, if it is not energizing then there is a problem with the relay.. Before you change out the expensive control board, try the therm..
Posted on Dec 09, 2008
I have a goodman GMP075-3 that won't turn on. I think it is the pressure switch since I do not have a vent blockage. What is a venter and where can I find it??
Posted on Dec 30, 2008
The board is bad. The unit thinks a flame is present, so it tells the blower to come on. Replace the board.
Posted on Oct 08, 2009
Maybe not! there is a limit switch that has opened not allowing power to pass and start the furnace. You will need to tale a Ohm meter and follow the wires thru any safety switch. In your case, it may be the thermo-disc near or over the burner box. Jump it out to test it. Now why is your blower not working (which could have been the reason why the thermo-disc opened)? Once you find which safety switch is open and you have jumped it out, take a jumper wire and jump between the R and G terminals on the circuit board. This should start your fan. If not, either the fan is stuck, the fan motor is bad or hopefully noy; the circuit board is bad.
Posted on Jan 18, 2010
Tips for a great answer:
Sep 28, 2016 | 2002 Dodge Ram Pickup 1500
Dec 13, 2013 | Goodman Manufacturing Goodman AEPF313716...
Jul 18, 2017 | Heating & Cooling
Nov 12, 2012 | Heating & Cooling
Nov 15, 2011 | Goodman Heating & Cooling
Oct 12, 2011 | Goodman GMS90703BXA Heater
Jan 22, 2011 | Heating & Cooling
Jan 02, 2010 | Goodman GMS90703BXA Heater
Oct 10, 2009 | Heating & Cooling
112 people viewed this question
Usually answered in minutes!