Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Heatpump A/C not working
First,Turn on the heat cycle (Not Emergency)and see if the outside unit come on,If not,and you don't have low voltage outside,Go to the inside unit and test the transformer,If you have low voltage from the transformer but not outside,It is the low voltage wires,If you don't have low voltage from the transformer,It's the transformer.If you have low voltage outside when in heat mode,but the unit won't come on,It's the contactor.Let me know if you need more help.
Please take time to rate this fixya
Posted on May 13, 2009
Tips for a great answer:
Aug 15, 2014 | Carrier 38CKC060 Air Conditioner
Nov 19, 2013 | Heating & Cooling
Dec 05, 2010 | Heating & Cooling
Jan 31, 2010 | Heating & Cooling
Oct 10, 2009 | Ruud Central System Air Conditioner
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
Feb 20, 2009 | Soleus KFR-18GW Split System Air...
Jul 21, 2008 | Haier Heating & Cooling
Jun 01, 2008 | Heating & Cooling
Jul 18, 2018 | Heating & Cooling
63 people viewed this question
Usually answered in minutes!