Question about Maytag Neptune MDE5500AY Electric Dryer
I have a sde3606ayw dryer I would like to use but the only nearby electrical source is a 120v/208v three phase panel. Will the dryer run ok on 208 volts? Will it pop a 30 amp breaker?
The nameplate says 120/240v 26amp 5757w 3wire
The dryer should work ok on 208 volts. The drying time may be a bit longer than usual since at 208 volts, you will only have 5408 watts of heat. Your bigger problem is your three phase panel. You can hook up one "hot wire" from the dryer to any of the three 3phase wires, and the other "hot wire" from the dryer to either of the two remaining 3phase connections and you will have a good connection to your dryer. However, the third wire from the dryer is a "ground wire" which has no connection in the three phase panel, or at least you didn't say it has one. If you can pull a ground wire from the grounding lug of the service panel feeding your 3phase box, and connect it to the third wire on the dryer, you would have a safe connection.
At 208v, the dryer will pull 26 amps. Be careful and make the right connections.
Posted on Jan 12, 2009
Tips for a great answer:
Jul 09, 2011 | Dryers
Apr 27, 2010 | Whirlpool LER5636P Electric Dryer
Mar 11, 2010 | Dryers
Jan 09, 2010 | Frigidaire GLER331A Electric Dryer
Nov 28, 2009 | LG DLE2532W Electric Dryer
Oct 13, 2009 | Kenmore Elite HE3 Steam 8674 Dryer
May 02, 2009 | Dryers
Apr 23, 2009 | GE DVLR223 Dryers
Oct 10, 2008 | Maytag Neptune MDE5500AY Electric Dryer
Sep 13, 2008 | Bosch Nexxt WTMC 3300 Electric Dryer
Aug 27, 2014 | Maytag Neptune MDE5500AY Electric Dryer
179 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: