Question about Heating & Cooling
I have Emberglow ventless gas logs (set to burn on porpane gas). First I connected them to a propane 20 lb tank and they worked perfectly (for about 2 hrs. until the tank lost pressure). Then I switched to a 100 lb. propane tank -like the manual recommends- and I get the pilot to ligth, but it will not stay on to start the logs. The propane tank is connected with a POL connector and a 1/2 psi regulator (11" CW) to a 5ft. 1/4" hose and a 3/8" connector (commercial kit) to a 1/2" black iron pipe that goes into the house.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Procom ML200TBA
Propane appliances usually run on 10-11 inches of water column, this is about 1/2 pound of pressure. If the regulator you have is not rated for delivering gas at that rate, you will need to find one that does. If your regulator is rated for more than the 11 inches, most likely you could have damaged the appliance regulator that came with the heater. Check the propane pressure specified by the heater manufacture against the rated supply of your regulator and see if they match. Make sure the heater is rated for Propane and NOT Natural Gas. Check to see if the gas valve on the appliance is in the operate position and all valves are open. Bleed off the air in the gas line by holding down the pilot switch and keep attempting to light the pilot. It could take you a few minutes. If you hear and smell gas but the unit will still not light, don't chance at getting hurt, call a technician. Look to make sure there are no safety switch that may have triggered off not allowing the gas valve to operate. And make sure there is no obstruction in the heater?s gas valve blocking off the supply of gas. Always exercise caution when it comes to gas and if you are uncomfortable, call a qualified gas technician.
Posted on Sep 17, 2007
Check the connection of the thermocouple or replace it if connections are tight.Pilot safety valve may be badreplace gas control valve.
Posted on Oct 24, 2009
sounds like your thermacouplar is going out and needs replaced. Sometimes these will act like they are working fine , but when the pilot stays on for awhile and later goes out it is a sure sign that it is bad
Posted on Nov 08, 2009
Sometimes when you turn a gas heater off for some time, if the source tank has been turned off, the line will bleed the propane and the line will contain mostly air. This is especially true if the supply line is long. In order to light the pilot, you will have to hold the pilot lighting button down for a while (a full minute or longer, depending on the size and length of the supply line) before pure propane arrives at the pilot light jet. You should keep a lighted lighter at the jet so that when the gas arrives, the lighter will light it. After the pilot lights, you will have to keep the button pressed long enough for the thermocouple to get hot enough to set the pilot to stay on. When it is hot enough, you should be able to release the pressed lighting button and the pilot should stay on. If it does, you should be able to light the heater. If the pilot jet never lights, gas is not getting to the regulator. If the pilot will not stay lit after a period of time waiting for it to heat the thermocouple, the thermocouple or the regulator may be bad and need replacement. :-)
Posted on Jan 03, 2010
Tips for a great answer:
Feb 08, 2014 | Emberglow Melbourne Oak 24 in. Vent-Free...
Dec 14, 2010 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Mar 31, 2010 | Heating & Cooling
Jan 07, 2010 | Desa International Unvented Gas Space...
Jan 03, 2010 | Desa International Unvented Gas Space...
Dec 12, 2009 | Desa International Unvented Gas Space...
Dec 03, 2009 | Desa International CCL3924PTA 24" LP Gas...
Nov 16, 2009 | Rinnai Desa Vent-Free Infrared Gas Heater:...
Oct 17, 2009 | Dyna-Glo Heating & Cooling
Nov 01, 2008 | Desa International CCL3924PTA 24" LP Gas...
407 people viewed this question
Usually answered in minutes!