Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
1) Turn the fan to on and if it runs you know that you have line
voltage to furnace and 24volts to the thermostat.
2) You could turn the furnace off remove the doors and get to the
control board. If you can find the Thermostat wires on the board
mark and remove them. If you have a typical Furnace and you
have some electrical background put a jumper wire between
terminals R and W,put the doors back on-there is a door switch
that if the panel is not put back on-it will not run. Turn your power
3) The Blower motor may come on, the induced draft blower should
come on, the glow coil should glow, the gas valve open and the
burners should come on and the unit should run.
4) If all of this happens, then you have a thermostat problem or you
have bad thermostat wires.
5) If nothing happens then you don`t have power to the furnace or the
little fuse that protects the transformer is blown.
Posted on Jan 08, 2010
Tips for a great answer:
Oct 12, 2016 | Heating & Cooling
Mar 20, 2014 | Brother P-touch PT-90 Personal Label Maker
Oct 02, 2013 | Toshiba Satellite L775d-s7340 17.3 Led...
Oct 13, 2012 | Honeywell Programmable Thermostat Heater
Jan 09, 2011 | Safe International Electronic Digital Safe...
Dec 04, 2010 | Honeywell Programmable Thermostat Heater
Oct 08, 2010 | Goodman GPC1342H21A Air Conditioner
Jan 18, 2010 | Universal Garage Wireless Keyless Entry...
Oct 29, 2009 | Honeywell Electronic Programmable...
Sep 13, 2005 | Dell Axim X5 Pocket PC
73 people viewed this question
Usually answered in minutes!