Question about Heating & Cooling
Yes.. first check circuit breakers on the outside unit. then.. make sure the power disconnect beside the outside unit is put in correctly. Sometimes a technition will replace them upside down. if you have power to the unit and it still has not came on.. make sure the unit is getting a "Call signal" from the thermostat. if there is a call signal from the thermostate reaching the outside unit, then listen for a "CLICK" when the thermostat is turned up and down. The click is the sound of the "COntactor" making contact when the unit recieves the "CALL Signal" This means the UNIT is most likely getting 220 volts, Check the voltage input to be sure with a Volt meter. IF you are still getting power and the unit is not running.. the run capacitor is most likely bad.
Posted on Jan 12, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 22, 2016 | LG Heating & Cooling
Jun 06, 2016 | Heating & Cooling
Apr 18, 2016 | LG LMN125HVT Air Conditioner
May 18, 2014 | LG LSC121PMA Split System Air Conditioner
Mar 10, 2014 | Whirlpool ACQ158XP Wall/Window Air...
Aug 22, 2011 | Heating & Cooling
May 02, 2010 | GE AJCQ08ACB Air Conditioner
Feb 21, 2018 | Heating & Cooling
63 people viewed this question
Usually answered in minutes!