Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Heat pumps have saftey circuits that prevent liquid flooding of the compressor. Inadequate airflow across the evaporator in cooling can trip this circuit. Have your package unit serviced with particular attention to cleaning the evaporator coil and be sure your filters are clean and changed frequently in the summer months. Hope this helps GL!
Posted on Jun 08, 2008
SOURCE: GE zoneline heat not working
Is it not heating in heat pump mode, emergency heat mode, or both? The default heat mode on the AZ55 is heat pump. Does the fan blow in heat mode? It's difficult to diagnose a heat pump with the information given. Since you say the unit cools, it's not a compressor problem. Possible problems could be reversing valve, thermostat, control board, or switch, if it is in heat pump mode. If it is running in emergency heat mode, problem could be switch, thermostat, control board, or heating element.
To determine if the unit is in HP or emergency heat mode, have a qualified technician check the auxiliary control switches. There are 2 sets of these. The set on the left, switch marked ALL I2R. If it is down, the unit is in HP mode, up is resistance heat. Hope this helps some.
GE Zoneline Specialist
Posted on Nov 11, 2008
If it was me I would cnage the sensor first. Simply because it is way cheaper than the control board and these sensors are fickle as hell to begin with.
Posted on May 14, 2009
Sorry to read about your problem, I hope this helps you out.
Sounds like you may a defective, reverse heat pump switch. If you were in Denver,Co I would be glad to work on it for you. They are no different than large units to work on.
and no, you cant work on the unit.....takes special tools
Just keep calling around for a person who will work on the unit..
I tried to help you. Please help me and Rate/Vote on my response. We take the time to answer your question. take the time to rate us.Thanks and good luck
4 Thumbs - Very Helpful
3 Thumbs - Helpful
2 Thumbs - Somewhat Helpful
1 Thumb - Not Helpful
Posted on Dec 27, 2010
SOURCE: i have a ''GE"heat &
Look at the wires that go to the compressor and make sure they are not burned off. Inspect the capacitor tops for swelling and loose or burnt wiring. Also check the connections coming from the controls. May have a wiring problem or even a bad compressor. How old is the unit?
Posted on May 17, 2011
Tips for a great answer:
Aug 15, 2014 | GE Zoneline Deluxe Series Cooling &...
Nov 05, 2013 | GE Zoneline AZ38H12DAD Split System Air...
Dec 27, 2010 | GE Zoneline AZ25E12D3B Air Conditioner
Dec 15, 2010 | GE Zoneline AZ55H07D Air Conditioner
Dec 14, 2008 | GE Zoneline AZ55H07D Air Conditioner
Oct 06, 2008 | GE Heating & Cooling
Jun 07, 2008 | GE Zoneline AZ38H12DAD Split System Air...
Jan 24, 2008 | GE Built-In Room Air Heat Cool Air...
Jan 10, 2008 | GE Zoneline AZ38H12DAD Split System Air...
60 people viewed this question
Usually answered in minutes!