Question about True 49 cu. ft. / 1388 liter Commercial Freezer GDM-49F-RC
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I'll try to give you the "Readers Digest" version.
First, make sure there is no ice build up on the evap. Light frost is O.K. as long as it does not effect air flow. (Very Important). All fans need to be running. Again, an air flow thing. There should be some product in the box but not too close to the evap. Again, an air flow thing.
The expansion device can effect your pressures to some degree i.e. Cap tube vs. TXV.
As a general rule of thumb, which I use almost everyday when it comes to pressures:
Low side is based on the temp difference between evap temp and condition space in the box. In freezers, it is almost always 10 degrees. If the box is 0 degrees then the evap needs to be at a minus 10 degrees. That is a pressure for R-404A of 24.5 psi. This only holds true when the temp in the box is approching set temp. I would say, about +10 degrees. 0 Degrees for the evap for R-404A is 33.5 psi.
High side should be ambient temp +30 degrees and then convert to a pressure for the refrigerant.
Example: 75 degrees in the room, +30 degrees equals 105 degrees. Now 105 degrees converted to a R-404A pressure is 253 psi. This will get you very close to the desired high side pressure.
I would look at low side first to see if it is within reason. Don't let the high side get too high. Increases the compression ratio and overworks the compressor.
Your icing problem could be a defrost issue and not a refrigerant charge issue.
Good Luck and hope this gets you started.
Posted on Apr 08, 2009
Tips for a great answer:
May 14, 2014 | Freezers
Aug 11, 2012 | Traulsen Reach in Freezer - G22010
Jul 31, 2011 | Whirlpool Freezers
Feb 28, 2011 | Freezers
Oct 03, 2010 | True 49 cu. ft. / 1388 liter Commercial...
Jul 24, 2010 | Freezers
Dec 16, 2009 | Delfield Freezer 6125XL-S
Aug 13, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Nov 23, 2008 | Freezers
Nov 01, 2007 | Freezers
344 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: